Yaskawa V1000 inverter is an extremely famous inverter in the world, this is a multi-purpose inverter with many outstanding advantages.
Today plc247.com would like to guide you to use HMI Weintek MT8071iE to connect Yaskawa V1000 inverter control via Modbus RTU communication
Wiring Diagram MT8071iE & V1000 VFD
Inverter Parameter Configuration
Here are the basic communication parameters we need to set
+ Control Run (0001H)
- Set 0001H = “1” >>> Forward Run
- Set 0001H = “2” >>> Reverse Run
- Set 0001H = “0” >>> Stop
+ Set Frequency: (0002H)
+ 0024H = 36 (dec)
+ 0025H = 37 (dec)
+ 0026H =38 (dec)
Weintek MT8071iE . Communication Configuration
We choose communication for MT8071ie according to inverter with parameters (9600/8/1/E)
When using Weintek HMI for Modbus-RTU communication, we have to add the register address 1 unit.
For example in this project the frequency register is 0002H + 1 = 0003H
Detailed programming instructions
+ Forward Button
+ Reverse Button
+ Stop Button
+ Setting Frequency
+ Output Frequency
+ Output Voltage
+ Output Current
Detailed Instruction Video
Software and supporting documentation
+ YASKAWA V1000 Manual PDF (password: plc247.com)
If you have any questions, please comment below the article, plc247.com will answer as soon as I read it.
Thanks and Best Regards!