Yaskawa V1000 series inverters feature compact design, high performance, quality and reliability. A new line of inverter technology that allows to control both asynchronous and synchronous motors.
It also supports various control methods. Today plc247.com will guide you to use HMI Proface GP4402WW to control Yaskawa V1000 via Modbus RTU RS485 Communication.
Yaskawa V1000 & GP4402WW “Wiring Diagram”
Yaskawa V1000 Modbus RTU Configuration
Below is a table of communication parameters that need to be installed for the inverter so that the inverter can be controlled by Modbus RTU
Registers Address Table
Note: GP4402WW HMI Address = “400001 (dec) + Device Address”
>>> Motor Control Address = 400001 + 1 = 400002
+ Set 400002 = 0000.0000.0000.0001 (Bin) = “1” >>> Forward Run
+ Set 400002 = 0000.0000.0000.0010 (Bin) = “2” >>> Reverse Run
+ Set 400002 = 0000.0000.0000.0000 (Bin) = “0” >>> Stop
>>> Frequency Reference Address = 400001 + 2 = 400003
- Output Frequency Address = 400001(dec) + 24(hex)
= 400001(dec) + 36(dec) = 400037
- Output Voltage Address = 400001(dec) + 25(hex)
= 400001(dec) + 37(dec) = 400038
- Output Current Address = 400001(dec) + 26(hex)
= 400001(dec) + 38(dec) = 400039
Proface GP4402WW Communication Setting
We need to set the communication parameters the same as those set in Yaskawa V1000
+ Main Interface
+ Frequency Setting Command
+ Forward Run Command
+ Reverse Run Command
+ Stop Command
+ Output Frequency Monitoring
+ Output Voltage Monitoring
+ Output Current Monitoring
Project Video Tutorial
Related Software and Documents
+ Yaskawa V1000 Manual PDF Download (Password Extract: plc247.com)
Please share the article to the community if you find it useful, subscribe to Youtube channel and Website to read the latest articles.
Thanks and Best Regards!