Yaskawa V1000 series inverters feature compact design, high performance, quality and reliability. A new line of inverter technology that allows to control both asynchronous and synchronous motors. The V1000 inverter parameter setting is easy, complying with international environmental standards.
Yaskawa V1000 supports control via I/O Terminal, Analogue and it also has a built-in RS485 port that supports control by Modbus-RTU Communication Protocol.
Siemens S7-200 & Yaskawa V1000 “Wiring Diagram”
Below is a diagram of Modbus RS485 communication connection between PLC Siemens S7-200 and Yaskawa V1000 inverter:
Yaskawa V1000 Modbus Parameters Setting
In addition to the basic parameters of the inverter (Frequency, voltage, current…) we need to install the following communication parameters so that Yaskawa V1000 can be controlled by Modbus communication protocol.
Yaskawa V1000 Registers Address Table
Note: Siemens S7-200 Holding Registers Address =
“VFD Address (Dec) + 40001”
>>> Motor Control Run Address = 1 + 40001 = 40002 (dec)
Set 40002 = 0000.0000.0000.0001 (Bin) = “1” >>> Forward Run
Set 40002 = 0000.0000.0000.0010 (Bin) = “2” >>> Reverse Run
Set 40002 = 0000.0000.0000.0010 (Bin) = “0” >>> Stop
>>> Frequency Setting Address = 2 + 40001 = 40003 (dec)
+ Output Frequency Address = 24 (hex) = 36 + 40001 = 40037 (dec)
+ Output Voltage Address = 25 (hex) = 37 + 40001 = 40038 (dec)
+ Output Current Address = 26 (hex) = 38 + 40001 = 40039 (dec)
PLC Modbus Programming
+ Communication Distribution
+ Port.0 Modbus Configuration
+ Frequency Setting Write
+ VFD Control Write
+ Data Monitoring
Project Video Tutorial
Related Software and Documents
Password Extract: plc247.com
If in the process of controlling Yaskawa V1000 inverter with Siemens S7-200 PLC using Modbus-RTU protocol, you need any support, please comment below the article, plc247.com will reply you as soon as I read the comments.