Hello everyone! In previous articles, we have used many different types of PLCs to control Delta MS300 inverters via Modbus-RTU RS485 communication standard.
Today plc247.com will guide you to use PC (using USB to RS485 port) to control DELTA MS300 inverter. This is a very fast way, we only need a few minutes to control the inverter as well as store data.
PC & DELTA MS300 “Wiring Diagram”
You can use any USB to RS485 port
DELTA MS300 VFD Communication Setting
In addition to the parameters of the inverter installed according to the motor (frequency, voltage, current), we need to set the communication parameters as follows:
+ P00.20 = 1 (Modbus-RTU Control Frequency)
+ P00.21 = 2 (Modbus-RTU Control Motor)
+ P09.00 = 1 (Address Slave = 1)
+ P09.01 = 9.6 (9600bps)
+ P09.02 = 0
+ P09.03 = 1.0 (Time Detect Err = 1.0s)
+ P09.04 = 14 (Modbus-RTU Slection 8bit / stop bit = 1/ Even)
>>> Motor Control Address = 2000 (hex)
+ Set Word 2000 = 18 (dec): Forward Run
= 34 (dec): Reverse Run
= 1 (dec): Stop Run
>>> Frequency Address = 2001 (hex)
- Output Frequency = 2103 (hex)
- Output Current = 2104 (hex)
- Output Voltage = 2106 (hex)
“Modbus Poll” Programming
+ Motor Control Command
+ Setting Frequency Command
+ Data Monitoring Command
Project Tutorial Video
Recommended software and documentation
Password Extract: plc247.com
Please subscribe to the youtube channel and share the article if you find it useful.
Thanks and Best Regards!